LogicsManagerTM. A large number of inputs, internal states, CAN values, or constant values can be combined logically to operate a relay contact or an internal. easYgen Series. easYgen – Installation. GR easYgen- – Configuration. GR easYgen – Operation this manual. German. easYgen Series. easYgen – Installation. GR easYgen – Configuration. GR easYgen – Operation.
|Published (Last):||1 July 2012|
|PDF File Size:||11.85 Mb|
|ePub File Size:||20.65 Mb|
|Price:||Free* [*Free Regsitration Required]|
Manual – overview Intended Use The unit must only be operated as described in this manual. Monitoring – standard values – generator overvoltage Current measuring – Generator, Phase Lx Page 10 5 Troubleshooting Page.
When shipping the unit sattach a tag with the following information: Using the these set points may be configured individually or combined to create a time range.
By pressing ‘print’ button you will print only current page.
Generator, Voltage Asymmetry The generator voltage asymmetry alarm measures voltage differences between the phases of the generator. The starter is engaged “Turning” display.
Move housing into panel 4. If your publication is not there, please contact your customer service representative to get the latest copy. The control unit may be identified from the numbers located on the unit and in the software. Manual easYgen – Genset Control Application: Pre-run auxiliary operation start preparation [t 0 to s Aux.
Flexible breaker configuration and start-stop logic Real and reactive power sensing Remote-start capability For more information, please visit here. This microprocessor-based, More information. Page 56 Page 57 – Protection: Obey all safety messages that follow this More information.
The engine, turbine, or other type of prime mover should be equipped with an overspeed overtemperature, or overpressure, where applicable shutdown device sthat operates totally independently of the prime mover control device s to protect against runaway or damage to the engine, turbine, or other type of prime mover with possible personal injury or loss of life should the mechanical-hydraulic governor s or electric control sthe actuator sfuel control sthe driving mechanism sthe linkage sor the controlled device s fail.
Critical Mode Sprinkler Op According to IEC three different characteristics are available. The display of parameters via the front panel will differ from the display of the parameters via the LeoPC1 program described in this manual. Woodward has a legacy as the “benchmark” in the distributed power generation industry for high-quality, reliable synchronizers, load sharing controls and generator controllers.
Woodward | Publications
Section – Wiring More information. The controller is exsygen specifically More information. Page 83 Manual easYgen – Genset Control The alarm classes have the following influence to the function of the unit. Generator, Voltage Phase Rot It is used to alert you to potential personal injury hazards.
Generator, Ground Fault Lim Page 12 Manual easYgen – Genset Control Relay outputs The discrete outputs can be grouped into two categories: Eawygen instructions More information.
Manual easYgen – Genset Control NOTE For the selection of the operating mode via the if two different operating modes have LogicsManager been selected simultaneously the control unit will prioritize the modes as follows: Current measuring – mains current Connect in application mode To print the manual completely, please, download it.
CAN bus Internal line termination The relay is enabled i. Could not add advanced results filter. The function may be changed by using the LogicsManager.
Woodward reserves the right to update easggen portion of this publication at any time.
If a loss of the supply voltage occurs, the relay contacts will not transfer and a fault condition will not be monitored. The stop solenoid remains energized for and additional 30 s after speed is no longer detected from the engine. Coils of operating current or undervoltage tripping devices, auxiliary contactors and power contactors must be wired with an appropriate interference protection.